
[Sponsors] 
July 16, 1999, 23:13 
CFD simulation on CO2 distribution

#1 
Guest
Posts: n/a

Dear all
I had conducted CFD simulation to investigate the CO2 distribution of an indoor space under four different exhaust air position. Relative ventilation efficiency: [CO2(exhaust)CO2(supply)]/[CO2(occuiped zone)CO2(supply)] is used to assess the ventilation performance. Obviouly, various ventilation efficiency were found for different exhaust air position. When I increase the generation rate of CO2 source by 10 times, the simulated ventilation efficiency almost remain unchanged. Is it true that the ventilation efficiency dependent on supply/exhaust air position, air flow pattern, etc. but independent of the generation strength of the CO2 source? Thanks a lot! Have a nice weekend! Apple Chan 17 July 99 

July 17, 1999, 05:57 
Re: CFD simulation on CO2 distribution

#2 
Guest
Posts: n/a

Hi, Apple,
>Is it true that the ventilation efficiency dependent on supply/exhaust air position, air flow pattern, etc. but independent of the generation strength of the CO2 source? If the CO2 source does not affect the velocity distribution, then yes. Indeed, CO2 concentration is governed by a linear equation, something like this dc/dt + u\nabla c =\nabla(diffusion coeff)\nabla c + source If you increase 'source' n times, you can easily see that, if 'u' is the same, new 'c' will be n times the old 'c'. Generally, source can also be in boundary and initial conditions. Look now at you definition of efficiency: if you multiply all quantities entering it by the same number, the fraction will not change. I am also somewhat surprised by this definition. Ventilation is usually expected to be working for a long time so that the process becomes steady. In that case, since CO2 cannot be accumulated, CO2(supply)=CO2(exhaust) and efficiency, as you defined it, is zero. Something similar I encountered when I was working on centrifuges cleaning oil in car engine. We defined efficiency to be proportional to something which in your case would look like CO2(content in the room)/CO2(supply) rate, with other quantities entering the formula to make it nondimensional. Hope this helps, Sergei 

July 18, 1999, 02:11 
Re: CFD simulation on CO2 distribution

#3 
Guest
Posts: n/a

Hi Sergei
Thank you for your response. First of all I have to apologize that I have not described my simulation in detail. Actually a CFD simulation for indoor air flow field was done before, i.e. a steady state of air flow field had been obtained. Then another CFD simulation was conducted using the aforesaid simulated flow field and adding CO2 generation source. Therefore the CO2 source does not affect the velocity distribution, as you mentioned. For the ventilation efficiency: [CO2(exhaust)CO2(supply)]/[CO2(occuiped zone)CO2(supply)], I think that I had not explained the meaning of each term clearly. In the room, fresh air with CO2 concentration: 400ppm [CO2(supply)] is supplied from air inlet. CO2 generation sources are located in the occupied zone. After well mixing from fresh air, CO2 concentration in the occupied zone will be simulated [CO2(occuiped zone)]. Then the air is exhausted through air exhaust outlet [CO2(exhaust)]. If this ventilation efficiency is greater than 1, that means it has good ventilation performance since most CO2 can be removed from the occupied zone and exhausted. If the ventilation efficiency is smaller than 1, that means "short circuit" occurs and most fresh air is exhausted through the air outlet directly without wellmixing with the air in the occupied zone. Could I have your comment please? Thank you very much! Have a good begining in this week! Apple Chan 18 July 99 

July 18, 1999, 10:05 
Re: CFD simulation on CO2 distribution

#4 
Guest
Posts: n/a

(1). In a room with a source, the source will stay at the same location if there is no convection and diffusion of the source. (2). When there is only diffusion in a room, the source will eventually fill the whole room. (3). The only way to remove the effect of the source is to use convection. (4). If you position a duct right in front of the source and apply the suction (low pressure) at the other end of the duct, then by convection, the source will be carried out through the duct and out of the room. The operation is just like the operation of a vacuum cleaner. You apply the suction on the source and remove it through the duct. (5). The operation is also similar to the operation of the kitchen range hood suction fan. In this case, there is a distance between the surface of the cooking surface and the entrance to the suction fan. Some diffusion effect will occur in this case. (6). In general, it is not a good idea to let the source to diffuse first because then you have a much larger volume to handle through the convection process. (7). I have studied and simulated 3D flow field of various range hood design for its effectiveness. And I hope that this will provide some help to your Co2 removal problem.


Thread Tools  
Display Modes  


Similar Threads  
Thread  Thread Starter  Forum  Replies  Last Post 
CFD Design...The CFD Future  John C. Chien  Main CFD Forum  20  November 20, 2015 00:40 
Solar Radiation in OpenFOAM  plainstyle  OpenFOAM Running, Solving & CFD  15  July 8, 2014 04:43 
Which CFD code for aerosol simulation  Andrea Panizza  Main CFD Forum  5  January 21, 2003 20:43 
ASME CFD Symposium  Chris Kleijn  Main CFD Forum  0  August 22, 2001 06:41 
3D Contaminant Dispersal Simulation  Apple L S Chan  Main CFD Forum  1  December 23, 1998 11:06 